Your Local Experienced Electrician in Ballarat and Nearby Areas!
Delacombe, Ballarat, VIC, 3356
SOLAR SYSTEM REPAIR
Can we please request a thorough solar health check. We believe that our solar system is not working due to a fault somewhere. Please send your Ballarat electrician to have a look at it.
January 9, 2020
We went out to check customer's solar system and we found it to have a faulty DC isolater. The solar system was not working so we replaced the DC isolater.